Due to changes to transmission path faults in AS1670.1:2015 (clause 2.6e), there is a requirement to split the audio output of the individual emergency zone amplifiers into audio multiple feeds.
If the audio is required to be split at the panel, then there is a 4-way audio splitter (154-0280), with each audio feed capable of handling up to 100watts. The total audio power handled by the splitter is 250watts. Each audio feed is individually supervised and isolated. Up to two 4-way splitters (8 outputs) can be connected to each 120W EV3000 Amplifier, and one 4 way splitter (4 outputs) can be connected to each 40W EV3000 Amplifier.
A power supply (154-0278) is required for every 10 4 way audio splitters.
If the audio is required to be split remote from the panel, then there is a 2-way remote audio splitter (4210-0143/111). The audio feeds can handle up to 60watts each, with a total of 120watts per splitter. Each audio feed is individually supervised and isolated, and passes the fault condition back to the EV3000 audio amplifier.
The 2-way Remote Audio Splitter is available as a DIN mount or enclosed version.
|4 Way Line Splitter|
|100VAC Line Outs||4 (Max 100W each - total 250W)|
|Monitoring||10K to 47KΩ 500mW EOL|
|2 Way Remote Splitter|
|Quiescent Current||17mAmps @ 16-30VDC|
|100VAC Line Outs||2 (Max 60W each - total 120W)|
|Monitoring||47KΩ 500mW EOL|
|Temperature||-20°C to 70°C|
|154-0278||EV3000 RJ45 Breakout Board (Power Supply)|
|154-0280||EV3000 4 Way Audio Splitter|
|4210-0143||EV3000 2 Way Remote Audio Splitter (DIN Mount)|
|4210-0144||EV3000 2 Way Remote Audio Splitter (Enclosed)|